<table class=" table table-striped">
<tbody>
<tr>
<td><strong>Standard/Long Backup Model</strong></td>
<td colspan="5">ITA-16K00AL1102P00 / ITA-16K00AL1202P00</td>
</tr>
<tr>
<td><strong>Nominal Rating (kVA)</strong></td>
<td colspan="5">16</td>
</tr>
<tr>
<td><strong>Nominal Input Voltage</strong></td>
<td colspan="5">380/400/415VAC 3-Phase,4Wire</td>
</tr>
<tr>
<td><strong>Input Voltage Range (V)</strong></td>
<td colspan="5">176-288VAC at full load; 100-176VAC at linear derating; 100VAC at half load</td>
</tr>
<tr>
<td><strong>Nominal Input Frequency (Hz)</strong></td>
<td colspan="5">50/60</td>
</tr>
<tr>
<td><strong>Input Frequency Range (Hz)</strong></td>
<td colspan="5">40-70</td>
</tr>
<tr>
<td><strong>Input Power Factor (kW/kVA)</strong></td>
<td colspan="5">0.99</td>
</tr>
<tr>
<td><strong>Current THD at Full Linear Load (THDi%)</strong></td>
<td colspan="5">≤5%</td>
</tr>
<tr>
<td><strong>DC Bus Voltage</strong></td>
<td colspan="5">288-480VDC</td>
</tr>
<tr>
<td><strong>Battery Charger Max Power (A)</strong></td>
<td colspan="5">13A (Long Backup) / 5A (Standard)</td>
</tr>
<tr>
<td><strong>Battery Option</strong></td>
<td colspan="5">P/C: ITA-BCI0020K01 (built-in battery module of 16 block × 12V × 9AH)</td>
</tr>
<tr>
<td><strong>Nominal Output Voltage (V)</strong></td>
<td colspan="2">220/230/240 (1-Phase)</td>
<td colspan="2">380/400/415 (3-Phase)</td>
</tr>
<tr>
<td><strong>Nominal Output Frequency (Hz)</strong></td>
<td colspan="5">50/60</td>
</tr>
<tr>
<td><strong>Rated Power Factor (kW/kVA)</strong></td>
<td colspan="5">Unity</td>
</tr>
<tr>
<td><strong>Voltage Harmonic Distortion (%)</strong></td>
<td colspan="5">&lt;2% for Linear Loads &amp; &lt;5% for Non-linear Loads</td>
</tr>
<tr>
<td><strong>Overload Capacity</strong></td>
<td colspan="5">At 25°C: 105% - 125%, 5min; 125% - 150%, 1min; 150%, 200ms</td>
</tr>
<tr>
<td><strong>Crest Factor</strong></td>
<td colspan="5">3:1</td>
</tr>
<tr>
<td><strong>Online Mode Efficiency</strong></td>
<td colspan="3">Up to 96.2%</td>
</tr>
<tr>
<td><strong>ECO Mode Efficiency</strong></td>
<td colspan="5">Up to 99%</td>
</tr>
<tr>
<td><strong>Dimensions</strong></td>
<td colspan="5">430 x 570 x 130</td>
</tr>
<tr>
<td><strong>Weight</strong></td>
<td colspan="5">23</td>
</tr>
<tr>
<td><strong>Noise at 1m (dBA)</strong></td>
<td colspan="4">≤58</td>
</tr>
<tr>
<td><strong>Operating Temperature (°C)</strong></td>
<td colspan="5">0 - 50</td>
</tr>
<tr>
<td><strong>Relative Humidity (%RH)</strong></td>
<td colspan="5">5 - 95, non-condensing</td>
</tr>
<tr>
<td><strong>Altitude (m)</strong></td>
<td colspan="5">~3000m</td>
</tr>
<tr>
<td><strong>General and Safety Requirements for UPS</strong></td>
<td colspan="5">IEC/EN 62040-1</td>
</tr>
<tr>
<td><strong>EMC Requirements for UPS</strong></td>
<td colspan="5">IEC/EN 62040-2</td>
</tr>
<tr>
<td><strong>UPS Classification According to IEC 62040-3</strong></td>
<td colspan="5">VFI-SS-111</td>
</tr>
</tbody>
</table>